Usage Registry Key
This specifies whether usage time is accumulated when the relay is in the
CLOSED state (1) or in the OPEN state (0). The key is set to 1 or 0
Note that certain relays may be reconfigured from Normally Open (NO) to
Normally Closed (NC) by jumper. This may affect the choice of metering
Set to enable an alarm when the associated usage meter reaches the Limit
Defines the alarm setpoint in hours and may include a fractional part. The
associated relay output goes into alarm when the usage meter reaches or
exceeds this setpoint.
This key may be optionally defined to enable services related to Relay
Output Usage Alarms.
This Registry key enables Usage Notification email.
CUSTOM EMAIL NOTIFICATION
This may be used define a block that creates a unique Usage Notification
This defines the amount of time in milliseconds that the Relay Output usage
alarm must remain clear before any subsequent usage alarm on this input will
be acted upon. The default is 300000 or 5 minutes.
When an alarm occurs the services associated with that event are performed.
The alarm must reset and remain so for this amount of time before those
actions would be performed again.
HELP Topics: EMAIL_BLOCK